Substation Commissioning Manual Essay
Application Areas 3
Safety Aspects 3
Cold Commissioning (GP - Step 108.4) 4
Check Readiness for Individual Tests (GP - Activity 108.4.1) 4
Perform Individual Tests (GP - Activity 108.4.6) 4
1. Outdoor Circuit Breaker (SF6) 4
2. Outdoor Disconnector 9
3. Current Transformer 11
4. Voltage Transformer 19
5. HV connections 23
6. Power Transformer 26
7. MV Cable 38
8. Substation Earthing Resistance 40
9. Interlockings 44
Hot Commissioning (GP - Step 108.5) 45
Check Readiness for Hot Commissioning (GP - Activity 108.5.1) 45
10. Start Up (GP - Activity 108.5.2) 46
This manual is intended to act as a handbook for commissioning works at substation site. The manual deals …show more content…
Check the tightness of the bolted connections for both the breaker itself and for the supporting structure. If any loose connections are found, tighten all the bolted connections to the right torque. Right torque values are stated in the breaker's installation manual.
1.4 Gas filling
If the breaker is not filled with gas, refer to the installation manual for the detailed instructions.
The alarm and blocking signals coming from the density monitor have to be checked. This is most convenient to do at the same time when the breaker is filled with gas. However if it is not done or you are not sure about it, it should be performed as a part of the commissioning works.
Mark the wires, if not done already, at the density monitor terminals and disconnect them. Remove the cable from the monitor. Remove the density monitor from the breaker. The breaker is equipped with back-flow barrier, so the monitor can be freely removed. Connect the monitor to